|Frequency:||868MHz Or 915MHz||Power Output:||1W|
|Distance:||5km||Output:||2 Analog Output|
|Technology:||Lora||Signal:||4-20mA Or 0-5V|
wireless on off module,
wireless cable transmitter
LS-RAO02-Lora wireless analog acquisition module
LS-RAO02-Lora Modbus RTU is a 1W I/O module, 2 analog outputs. Wireless control around 5km LOS. Use for sensor and PLC/HMI wireless communication
Using Lora 1W data module inside, it is OK to control around 5km. This wireless analog module is good for sensor data wireless collection.
Lensen wireless analog I/O module helps you build wireless connection between sensors with PC/PLC. It is to transmit Welcome to contact our sales for more details.
|Input type||4-20mA or 0-5V or 0-10V|
|Output type||4-20mA or 0-5V or 0-10V|
|Resolution ratio||24 bit|
|Power supply||9-36V DC usually use 24V DC|
|Channel No.||16ch default, can program via DIP switch|
|Antenna||Sucker antenna with 1.5m cable|
|Working temperature||-35 °C ~ +75 °C industrial|
|Working humidity||10%-90% relative humidity, no condensation|
|Fix way||Standard 3.5 inch industrial DIN guild rail|
Wireless pump controls
Automate your tank level without running wire between the well pump and the tank. Wireless pump controls save you time and money.
Wireless tank level monitoring
simple wireless monitoring of your tank level from a remote location and receive critical status updates.
Wireless valve activation
Open or close electronic wireless valves, solenoid valves.
Pivot irrigation, soil pressure and temperature monitoring
Receive critical status updates by email, phone, cell phone, or PDA if equipment fails
Control a conveyor motor remotely
Remote Control Relay
Use dry contact inputs to control a remote relay.
Save time in large facilities by activating an overhead notification light when a problem occurs, letting the supervisor know exactly where to go.
Use wireless I/O module to operate your dust
Wirelessly acquire and log various data from a remote location using our analog I/O module
Start and stop your stacker/reclaimir. Connect PLC in control center with stacker and reclaimer.
Mount a transmitter with adjustable range on heavy equipment, mount a receiver in a “blind spot,” and then set up the receiver to sound an alarm or turn on a light whenever the equipment is operating in the area.
Chemical Level Monitoring
Monitor water chlorination or other chemicals remotely.
Avoid having to lay new wire by using wireless transmitters and receivers to control traffic signs such as “Railroad Crossing Ahead” when a train is present.
Our wireless transmitters and receivers can be used to monitor grain elevator conditions or control different functions. To collect RS485 data. To monitor temperature and humidity in Grain.
Digital I/O module for crane control and analog I/O module to send the load information wirelessly to another location.
Modbus RTU communication and corresponding value
|Register types||Read command|
Input --not support
|Not keep||Can read input value|
A. Hold register
1. Analog input value: 0x0008~0x000B
2. Analog output value: 0x0048~0x004B
B: How to read
Hold register: can read 4 analog input or control 4 analog output at one time
Register control way
|Function ID||items support|
|No.||IC Type||PLC ID||Modbus ID|
About value calculation
Our analog module’s max measure range value is : 0X7FFF
1. Directly measure current and voltage
Exact value=value you read/0x7FFF*max range
For example: to read the 1st passage of module’s (with max range of 0-20mA) input value
Register 0x0008(analog input of the 1st passage)
Current value: (0x3801/0x7FFF)*20mA=8.7509mA
2. To measure sensor’s value(4-20mA, 0-6 meter level sensor)
If feedback value is less than 6554, level value is 0
If feedback value is bigger than 6554, level value=(value read-6554)/(32767-6554)*measure ranges
For example: feedback value is 0X3801, then corresponding level value is: ((0X3801-6554)/26213)*6 meter=1.7815 meter
Analog module’s max measure range is: 0x7FFF
Directly control output current and voltage
Write register value=current or voltage value/measure range*0x7FFF
For example: to control the 1st passage of analog module whose max measure range is 0-20mA
Register 0x0048 (analog output of the 1st passage)
To write register value:(8.75/20mA)*0X7FFF =14336=0x3800